Commercial Fluoride Removal Water Filters for 22-280 gpm flow. System utilizes a strongly basic hybrid anion exchange resin specially formulated to selectively remove fluoride. Our Industrial Fluoride Water Filters exhibit large throughput capacity in arsenic removal on potable or drinking water supplies. Performance is virtually unaffected by common anions, such as chlorides, bicarbonates or sulfates. The system is effective over the entire pH range of potable water.
Commercial Fluoride Removal Systems are designed to effectively remove fluoride from drinking water.
Commercial Fluoride Removal Water Filters features:
Can be used with standard Fleck® electronic controls or with a mechanical control
Heavy duty structural tanks - Poly Glass mineral tank
All brass, motor driven control valve with fully adjustable regeneration cycles (on units with electronic control valve)
Self adjusting backwash control (on units with electronic control valve)
Flow controller to limit backwas flow
Engineered for commercial and industrial use
Optional skid mounting for tanks
Available water flow is between 22 GPM and 280 GPM (gallons per minute).
5 year Warranty on all Fleck control valves.
10 year Warranty on media tank.
All units can be assembled with or without automatic backwash valve. Contact us for price information on manually backwashed units.
These units are heavy! Actual shipping charges will be added to your order after unit is assembled. A very rough estimate (we express no guarantees if this price is accurate on the date of order!) of shipping charges would be between $180 and $500 (continental US), and can vary greatly based on model, your zip code, location, availability of lift gate, fork lift, and gas prices. LTL Freight shipping out of Atlanta, Georgia.
Backwashing time is 10 minutes.
Table below will help you to identify system for your application. Look for water line size (Pipe Size) and Peak Flow in gallons per minute (GPM), and choose an appropriate model. Also, you can estimate fluoride removal at 2 gpm (very conservative) to 6 gpm per cubic foot of media. For instance, if flow is 40gpm, conservatively you'd need a 20 cubic foot tank, but may be able to do the job with a 7 cubic foot tank.
|Capacity (Gallons) at 5 mg/L in influent with below 2 mg/L in effluent
|Peak Flow, GPM
|Mineral Tank Size, in.
|Service Flow, GPM
|Backwash Flow, GPM
|Space Required, in. (WxDxH)
|Shipping Weight, lbs
Fluoride Removal Water Filter control valves: