Commercial Granular Activated Carbon Water Filters ( GAC ) are designed for outstanding pefrormance, and are ideal for removing chlorine, organics, chloramines, colors, odor, THMs and Volatile Organic Compunds ( VOCs ) from water. They are cost effective and reliable.
Our Commercial GAC Water Filters use patented Eagle Redox Alloy ® to significantly increase lifespan of GAC filter and prevent bacteria contamination. Eagle Redox Alloy is a copper-zinc formula that is completely safe to operate and meets EPA and FDA standards for level of zinc and copper in potable water.
As a side benefit, redox consistently removes 99% of free chlorine, and also removes lead, mercury, iron and hydrogen sulfate. The media inhibits bacteria growth (fungi, algae and mold) and reduces lime scale, mold, and fungi. throughout the entire unit. In fact, testing has shown that it reduces it up to 90%; thus eliminating the need for silver, commonly used in carbon-only filters.
GAC Commercial / Industrial Water Filters features:
Can be used with standard Fleck® electronic controls or with a mechanical control
Heavy duty structural tanks - Poly Glass mineral tank
All brass, motor driven control valve with fully adjustable regeneration cycles (on units with electronic control valve)
Self adjusting backwash control (on units with electronic control valve)
Flow controller to limit backwas flow
Engineered for commercial and industrial use
Optional skid mounting for tanks
Available water flow is between 22 GPM and 280 GPM (gallons per minute).
5 year Warranty on all Fleck control valves.
10 year Warranty on media tank.
All units can be assembled with or without automatic backwash valve. Contact us for price information on manually backwashed units.
These units are heavy! Actual shipping charges will be added to your order after unit is assembled. A very rough estimate (we express no guarantees if this price is accurate on the date of order!) of shipping charges would be between $180 and $500 (continental US), and can vary greatly based on model, your zip code, location, availability of lift gate, fork lift, and gas prices. LTL Freight shipping out of Atlanta, Georgia.
Q: How often do you need to replace carbon media?
A: To calculate replacement interval in gallons, multiply number of cubic feet by 500,000 gallons
Table below will help you to identify system for your application. Look for water line size (Pipe Size) and Service Flow in gallons per minute (GPM), and choose an appropriate model.
|Peak Flow, GPM
|Service Flow, GPM
|Mineral Tank Size, in.
|Backwash Flow, GPM
|Space Required, in. (WxDxH)
|Shipping Weight, lbs
Commercial GAC Water Filter control valves: